Eterna Battery Replacement Service
Like most competitors, we are unable to include batteries in extended warranties, but do feel it’s unfair & not environmentally friendly that good fittings become redundant due to the battery reaching the end of its life.
We would firstly suggest that you follow our maintenance guidance (see below) on emergency products to maximise battery life, but would also like to offer the reassurance of a battery replacement service to support our current emergency product offer – we will try to help with legacy products but cannot guarantee availability.
Please note that in the unlikely event your new fitting is supplied with a faulty battery, we will replace the battery free of charge subject to our terms and conditions.
WE ONLY RECOMMEND ETERNA REPLACEMENT BATTERIES WITH ETERNA EMERGENCY PRODUCTS
|Code||Battery Description||Eterna Product Code|
|EB1||Ni-Cd 3.6V 1500mAh Stick Battery||EML3MISO EML3NMISO EMLED3M EMLED3NM SEEMLED3M|
|EB2||Ni-Cd 3.6V 2000mAh Stick Battery||ELEGAN5EM3 LDLEM3 SELB4FTEM3 SELB5FTEM3 SELB5HOEM3 SELB6FTEM3 SELB6HOEM3 SELDLEM3|
|EB3||Ni-Cd 3.6V 6Ah Side-by-side Battery||LEDTWNSPOT SELTWNSPOT|
|EB4||Ni-Cd 3.6V 1500mAh Side-by-side Battery||EXIT3MLED EXIT3MLISO SEEXIT3ML LEDREM3|
|EB5||Ni-Cd 3.6V 4.5Ah Stick Battery||EBPM3 SEEBPM3 VECOBPACK VECOPANEM3|
|EB6||Ni-Cd 3.6V 1300mAh Stick Battery||SLIMBHEM3M|
|EB7||Ni-Mh 3.6V 2000mAh Side-by-side Battery||EBLSLIMM|
|EB8||Ni-Cd 3.6V 800mAh Side-by-side Battery||EXITMMO SESIGNLEM3 SIGNLEDEM3 SIGNEM3ISO|
|EB9||Ni-Cd 4.8V 600mAh Side-by-side Battery||LEDMDDEM3 LMDDEM3ISO SELMDDEM3|
|EB10/2||Ni-Cd 6V 2000mAh Side-by-Side Battery||WPLEDEM351 WPLEDEM352 WPLEDEM361 WPLEDEM362 WP51SDEM3 WP61SDEM3|
|EB11||Li-ion 3.2V 1500mAh Stick Battery||ALEM3BKEYE ALEM3BKFUL ALEM3BKGRI ALEM3WHEYE ALEM3WHFUL ALEM3WHGRI ALMF3BKEYE ALMF3BKFUL ALMF3BKGRI ALMF3WHEYE ALMF3WHFUL ALMF3WHGRI CFLWHEM3SC CHA18EM3 CHA18MW3 CHA18SDEM3 CIROPALEM3 CIROPALMW3 CIRPRISEM3 CIRPRISMW3 CO12EM3 CO12MW3 CO12SCEM3 CO12SCMW3 CO18EM3 CO18MW3 CSLEDCREM3 CSLEDWHEM3 KCIREM3 KCIRMW3 MSCSLCREM3 MSCSLWHEM3 MSLWHEM3SC SDCSLCREM3 SDCSLWHEM3 SDLEDCREM3 SDLEDWHEM3 SQOPALEM3 SQOPALMW3 SQPRISEM3 SQPRISMW3 OPCIREM3 OPCIRMW3 PRCIREM3 PRCIRMW3 OPSQEM3 OPSQMW3 PRSQEM3 PRSQMW3|
|EB12||Ni-Cd 3.6V 1500mAh Stick Battery||VECOBHEM3M VECOEM3M|
|EB13||Ni-Cd 3.6V 4000mAh Side-by-side Battery||VECOTWINSP|
|EB14||Ni-Cd 3.6V 1800mAh Stick Battery||DB3MLED|
|EB15||Ni-Cd 3.6V 2Ah 3-Linked Battery||SESMDLEM3|
|EB16||Ni-CAD 3.6V 4.5Ah Side by Side Battery||TSPOTLIP20|
|EB17||Li-Ion 3.2V 1500mAh Stick Battery||KEM3BULKLI VECOEXIT3M KEXIT3MLI|
|EB18||Li-Ion 3.2V 4500mAh Side-by-Side Battery||KTWINSPLI SETSPOT|
|EB19||Li-Ion 3.2V 1500mAh Stick Battery||LDLEM3LI SEMEM3 KEM3LIDL|
|EB20||Li-Ion 6.4V 1500mA Stick Battery||EBPM3LI KBATPLI KWPEM3SIN5 KWPEM3SIN6 KWPEM3TWI5 KWPEM3TWI6 WP41EM3 WP41MW3 WP51EM3 WP51MW3 WP52EM3 WP52MW3 WP61EM3 WP61MW3 WP62EM3 WP62MW3 BATL4FTEM3 BATL5FTEM3 BATL5HOEM3 BATL6FTEM3 BATL6HOEM3|
|EB21||Ni-Cd 3.6V 800mAh Stick Battery||VECOMEM3 VECOMEM3L KEM3ML|
|EB22||Li-Ion 3.2V 1000mAh Stick Battery||DLSTEM3|
|EB23||Li-Ion 3.2V 1000mAh Stick Battery||KEM3BULKLI|
|EB24||Li-Ion 3.2V 1000mAh Stick Battery||SEMEM3|
|EB25||Li-Ion 3.2V 1000mAh Stick Battery||KEXIT3MLI SEEXITLI VECOEXIT3M|
IMPORTANT OPERATIONAL CHECKS TO KEEP YOUR FITTING WORKING:
Periodic testing should be carried out to ensure emergency lighting is operating correctly. For the period of the test, isolate the power supply by operation of a key switch, or other isolation device. At the end of the test, power should be restored and all indicator lamps checked.
- DAILY: Visual inspection of the battery charge LED.
- EACH MONTH: Isolate the power supply for a period sufficient to ensure that each lamp is illuminated. Endorse the test record form supplied.
- ONCE EACH YEAR: Isolate the power supply and check that the light is still illuminated after 3 hours. Endorse the test record form.
If after routine operation check, the lamp does not remain lit for the three hour period, a new battery pack may be required.
- Switch off the electricity at the mains, both switched and permanent supply.
- Allow batteries to fully discharge then reconnect to supply and allow to charge for 24 hours.
- Test again for 3 hours, if light does not remain lit change the battery pack.
- Check install guides for procedure on changing the battery.